Honeywell Thermostat with a Goodman Air Conditioner / Heat Pump How Do I Hook it Up????
*The L (relay) terminal is powered continuously when thermostat is set to Em Heat.
The Honeywell guide also states to use either O or B terminals for changeover valve and install field jumper between E and Aux if there is no emergency heat relay.
The Goodman 3 ton package unit with heat pump and 15kw heat strip has wires colored... Red (24v), Green (fan), Orange (Rev. valve), White (Heat 2nd), Brown (Heat 3rd), Yellow (cool), Blue (common).
So, the main question is how do I make these connections up and what is the difference between the Auxiliary Heat Relay and the Emergency Heat Relay?
Any and everyones help is greatly appreciated.